o Compact size
o Excellent microprocessor control guarantees high reliability
o Boost and buck AVR for voltage stabilization
o Auto restart while AC is recovering
o Simulated sine wave
o Off-mode charging
o Cold start function
o Generator compatible (option)
400 VA / 240 W
600 VA / 360 W
800 VA / 480 W
110/120 VAC or 220/230/240 VAC
81-145 VAC / 162-290 VAC
60/50 Hz (Auto sensing)
110/120 VAC or 220/230/240 VAC
AC Voltage Regulation (Batt. Mode)
Frequency Range (Batt. Mode)
50 Hz or 60 Hz ± 1 Hz
Typical 2-6 ms
Waveform (Batt. Mode)
Simulated Sine Wave
Battery Type & Number
12 V/4.5 Ah x 1
12 V/7 Ah x 1
12 V/9 Ah x 1
Typical Recharge Time
4 hours up to 90% capacity
Overload, discharge, and overcharge protection
Sounding every 10 seconds
Sounding every second
Sounding every 0.5 second
Dimension, D x W x H (mm)
279 x101 x142
Net Weight (kgs)
0-90 % RH @ 0- 40°C (non-condensing)
Less than 40dB
* Product specifications are subject to change without further notice
The following items are inside the box:
Remove the UPS from its package and inspect it for damage that
may have occurred during shipping. If any damage is discovered,
re-pack the unit and return it to the place of purchase.
2）、Connect to Utility Power
Connect AC power cord to utility power. Then, the UPS will start to
charge inside battery. For best result, charge the battery for 6 hours
prior to initial use.
3）、Plug in Equipment
Plug your equipment to Battery Backup Outlets on the rear panel of
NOTE: Make sure that the UPS is powered on to protect all
important devices from data loss during power failure.
CAUTION: NEVER connect a laser printer or scanner to the
battery backup outlets of UPS. The equipment may draw
significantly power to overload the UPS.
2、OPERATION & FUNCTIONS
1)、Turn On the UPS
To turn on the UPS unit, press the power switch lightly. Then, the
LED will light up.
2）、Turn Off the UPS
To turn off the UPS unit, press the power switch again. Then, the
LED will go off.
3）、Cold Start Function
When the UPS is off and there is no power utility, it's still possible to
cold start the UPS unit to power the loads.
4）、Free Software Download (Option)
Go to the website http://www.power-software-download.com and
download the ViewPower software. Follow on-screen instruction to
install the software. When your computer restarts, the monitoring
software will appear as an orange plug icon located in the system
tray, near the clock.
A)、Battery backup outlets:
Plug sensitive equipment into battery backup outlets. Battery
power is automatically provided in case of a power outage.
The fuse will be burned out if an overload condition forces the UPS
to disconnect itself from utility power.
D)、USB com. port (option):
To monitor the UPS status, such as unattended UPS shutdown and
start-up, by using download software, please connect the UPS and
PC with USB cable included.
E)、Modem/Phone line surge protection (option):
Connect a single modem or phone line into surge-protected “IN”
outlet on the back panel of the UPS unit. Connect from “OUT”
outlet to the computer with another phone line cable.
When the UPS is in battery backup mode (battery mode), the
green LED will flash and the UPS sounds an audible alarm every 10 seconds.
When the UPS is in battery backup mode (battery mode) and the
battery energy begins to run low, the UPS will beep every second.
When the UPS is overloaded, the UPS will beep every 0.5 second
to warn an overload condition.
When there a UPS fault occurs, the UPS will continuously beep.
SAVE THESE INSTRUCTION-This manual contains important instructions that should be followed during installation and maintenance of the UPS and batteries.
1）This UPS utilizes voltage that may be hazardous. Do not
attempt to disassemble the unit. The unit contains no user
replaceable parts. Only factory service personnel may perform repairs.
2) This pluggable type A equipment with battery already installed
by the supplier is operator installable and may be operated by laymen.
3) The mains socket outlet that supplies the UPS shall be
installed near the UPS and shall be easily accessible.
4) During the installation of this equipment it should be assured
that the sum of the leakage currents of the UPS and the
connected loads does not exceed 3.5mA.
5) Connection to any other type of receptacle other than a
two-pole, three-wire grounded receptacle may result in shock
hazard as well as violate local electrical codes.
6) In the event of an emergency, press the "OFF" button and
disconnect the power cord from the AC power supply to
properly disable the UPS.
7) Do not allow any liquids or any foreign object to enter the
UPS. Do not place beverages or any other liquid-containing
vessels on or near the unit.
8) This unit intended for installation in a controlled environment
(temperature controlled, indoor area free of conductive
contaminants). Avoid installing the UPS in locations where
there is standing or running water, or excessive humidity.
9) Do not plug the UPS input into its own output.
10)Do not attach a power strip or surge suppressor to the UPS.
11) Do not attach non-computer-related items, such as medical
equipment, life-support equipment, microwave ovens, or
vacuum cleaners to UPS.
12)Do not dispose of batteries in a fire as they may explode.
13) A battery can present a risk of electrical shock and high short
circuit current. The following precautions should be observed
when working on batteries:
(1) Remove watches, rings, or other metal objects from the hands.
(2) Use tools with insulated handles.
(3) Wear rubber gloves and boots.
(4) Do not lay tools or metal parts on top of batteries.
(5) Disconnect charging source prior to connecting or
dis-connecting batteries terminal.
14)Internal battery voltage is 12VDC.Sealed, lead-acid, 6-cell
15) Servicing of batteries should be performed or supervised by
personnel knowledgeable of batteries and the required
precautions. Keep unauthorized personnel away from batteries.
16) When replacing batteries, replace with the same number and
type of sealed lead-acid battery.
17) Do not open or mutilate the battery or batteries. Release
electrolyte is harmful to the skin and eyes. It may be toxic.
18) Attention, hazardous through electric shock. Also with disconnection
of this unit from the mains, hazardous voltage still
may be accessible through supply from battery. The battery
supply should be therefore disconnected in the plus and minus
pole at the connectors of the battery when maintenance or
service work inside the UPS is necessary.
19) To reduce the risk of overheating the UPS, do not cover the
UPS' cooling vents and avoid exposing the unit to direct
sunlight or installing the unit near heat emitting appliances such
as space heater or furnaces.
20) Unplug the UPS prior to cleaning and do not use liquid or spray
6、PLACEMENT & STORAGE:
Install the UPS in a protected area that is free of excessive dust
and has adequate air flow. Place the UPS away from other units at
least 20 cm to avoid interference. For best performance, keep the
indoor temperature between 0° C and 40° C.
All connected equipment should be turned off, then disconnect
from the UPS to avoid battery drain. Unplug the UPS from the wall
outlet. Then turn off the UPS for storage. Store the UPS unit
covered and upright in environments where the ambient
temperature is -20 C to 50 C with its battery fully char